urisaf 1000 Tablets Make Water Safer to Drink FAST
Each Purisaf 1000 tablet gives 1000 ppm available Chlorine in 1 Litre of Water.
One tablet will disinfect 200 Litres of water at 5 mg/L (5 ppm/L) Chlorine or 250 Litres of water at 4 mg/L (4 ppm/L) Chlorine.
Accurate and Easy Dosing, Versatile and Fast Acting for use in:
Water Towers and Wells
Camping, Caravaning & Boating
Spring Water and Storage Bowsers
Spring Boxes or Silt Traps
TOP TIP: Warm Water speeds up tablet dissolution time. Pre-dissolve in a little warm water then pour into the usable water for the solution.
Purisaf 1000 Water Purification Tablets are equivalent to more expensive brands such as Oasis 1000. Often, the brands disguise the product by using terminology that seems confusing – here is our guide to help:
Technical: Contains Sodium dichloroisocyanurate (sometimes referred to as Troclosene sodium, Abbrev- NaDCC).
Synonyms: Sodium Dichloro -1,3,5 – Triazinetrione Anhydrous. Sodium Dichloro – S – Triazine -2,4,6 1H,3H,5H)-Trione. Troclosene Sodium.
EC/EINECS No.: 220-767-7
Chemical Name: 1,3,5 – Triazine -2,4,6 (1H,3H,5H) Trione 1,3, – Dichloro, Sodium Salt
Chemical Family: Chlorinated S Triazine Trione
Export Tariff: 3808 9420
Please click on link below to download Safety Data sheet.
DS001 PN501 Chlorine Tablets REV 12
Well Water – new or contaminated
Make up 25 tablets in 25 Litre solution
Pour half into the well, operate pump until Chlorine is detected.
Stop pumping and add remainder of solution to well.
Leave for minimum of one hour.
Pump again, ensuring all domestic taps are open.
Check for Chlorine smell at each tap, then turn off.
Wait 12 hours before checking for a minimum of 2mg/litre (2ppm chlorine/Litre)
Refill the system with potable water.
Spring Boxes or Silt Traps
Make up 25 tablets in 25 Litre solution.
Using half the solution thoroughly scrub inside walls with the Chlorine solution paying particular attention to the highest and lowest water line levels.
P:our remaining half of the solution into the Box/Trap.
If there is a pump, repeat steps 4 to 8 (see Well Water Instruction above.
Chlorine odour can linger and this may take a few days to disappear.
Always test for residual Chlorine smell or Chlorine reading before drinking. If no residual Chlorine smell, retreat. Ground water ill invariably be cleaner than surface water.
Water Source Conditions to be aware of:
Faecal contamination is VERY DANGEROUS – avoid if suspected.
Industrial pollution – avoid if suspected.
Foul smelling water – possible algae contamination. Filter if possible
Turbidty – if Turbidity measures NTU 5 or above then water must be filtered.